Views
4 months ago

# 2016_Title24_Nonresidential_Lighting_Guide_170419_web_0-99-109

## APPENDIX Table 140.6-E:

APPENDIX Table 140.6-E: Adjustments for Mounting Height Above Floor Height in feet above finished floor and bottom of luminaire(s) Floor Display or Wall Display — Multiply by < 12' 1.00 12' to 16' .87 > 16' .77 Table 140.6-F: Room Cavity Ratio (RCR) Equations Determine the Room Cavity Ratio using one of the following equations Room cavity ratio for rectangular rooms RCR = 5 x H x (L + W) L x W Room cavity ratio for irregularly shaped rooms RCR = 2.5 x H x P A H =Vertical distance from the work plane to the center line of the lighting fixture L = Length W = Width P = Perimeter A = Area of the room 108 2016 BUILDING ENERGY EFFICIENCY STANDARDS

APPENDIX Table 140.6-G: Illuminance Level (Lux) Power Density Values (W / ft 2 ) Illuminance Level (lux) RCR ≤ 2.0 RCR > 2.0 and ≤ 3.5 RCR > 3.5 and ≤ 7.0 RCR > 7.0 50 0.18 0.22 0.32 0.46 100 0.3 0.38 0.56 0.84 200 0.48 0.64 0.88 1.34 300 0.64 0.82 1.12 1.76 400 0.78 0.98 1.34 2.08 500 0.9 1.10 1.52 2.32 600 1.06 1.26 1.74 2.6 700 1.24 1.46 1.82 2.96 800 1.44 1.7 2.28 3.30 900 1.66 2.0 2.64 3.74 1,000 1.84 2.2 2.90 4.06 NONRESIDENTIAL LIGHTING GUIDE 109

1JM3IEs
licht.wissen No. 06 "Shop Lighting - Attractive and Efficient"
General information, optic specifications, index
Industry/Logistics. Light solutions that really work. - Osram
Lighting
Office Lighting - Illuminating Engineering Society
licht.wissen No. 05 "Industry and Trade"
Brighter Pupils - THORN Lighting
Lightcolumns Brochure - Gardco Lighting
Luxonic Lighting
Arcturus-15 Brochure - Sterner Lighting
Green Building Lighting Practices - Alive2green
licht.wissen No. 13 "Outdoor workplaces"
PL Series 1 LED Luminaires 6-page Brochure - Selecon
CO1048 - Columbia Lighting
CO1048 - Columbia Lighting
Everything must go - Lux magazine
APPLICATION GUIDE LIGHTING CONTROL SYSTEMS
APPLICATION GUIDE LIGHTING CONTROL SYSTEMS - Nortronic
LIGHTFAIR 2009 - Illuminating Engineering Society
licht.wissen No. 04 "Office Lighting: Motivating and Efficient"
DL-BR_News2013_EU-High
Exterior Lighting 2012/2013 - Fergin AB
HACCP-/ IFS-LEUCHTEN
Energy efficient and biological aspects in renovation of auditorium ...
Ballasts with constant luminous flux
FL800 LED - CU Phosco
ARES 2017 Catalogue